|Posted on March 9, 2016 at 11:10 AM||comments ()|
Excerpts below are from an HVAC HESS publication from September entitled "The Importance of Cleaning Coils"
Finned coils are used in a number of different applications in HVAC systems to transfer heat either into or out of air streams. There are two basic types of coils:
1. Cond ense r coils - Condenser coils transfer heat into a space. Refrigerant vapor is forced into the coil under pressure, condensing the refrigerant into a liquid, which results in the rejection of heat across the heat exchange surface.
2. Evaporator coils - Evaporator coils do the opposite to condenser coils. Liquid refrigerant is pumped into a low pressure coil, causing the refrigerant to evaporate into a vapor, absorbing heat across the heat exchange surface in the process.
Over time the surfaces of these coils can become dirty as the air moving over the coils can contain dust, dirt, pollen, moisture and other contaminants. A build-up of contaminants decreases the available surface area for heat transfer, reducing the EFFICIENCY OF THE HEAT TRANSFER PROCESS. LEADING TO EXCESSIVE energy consumption and poor system performance. It is important that air conditioning coils are regularly inspected AND MAINTAINED TO ENSURE THEY OPERATE AT OPTIMUM EFFICIENCY.
IN ADDITIONTO THE ENERGY EFFICIENCYAND SYSTEM PERFORMANCEBENIFITS, REGULAR COIL CLEANING ALSO IMPROVES EQUIPMENT LIFE SPANS and indoor air quality; a fact that has led to regular coil cleaning becoming a regulatory requirement in certain circumstances.
Dirty condenser and evaporative coils have a negative impact ON ENERGY EFFICIENT HVAC SYSTEM OPERATION.
ACCORDING TO THE US Department of Energy (DOE) “a dirty condenser coil can increase compressor energy consumption by 30%”. A dirty CONDENSER COIL CAN INCREASE COMPRESSOR ENERGY CONSUMPTION BY 30%. A DIRTY EVAPORATOR COIL WILL DECREASE AIRFLOW WHICH REDUCES HEAT TRANSFER THEREBY DEGRADING THE DEHUMIDIFICATION PROCESS
Although the drop in capacity is not as large with dirty condenser COILS AS IT IS WITH DIRTY EVAPORATOR COILS, THE COEFFICIENT OF
performance (COP) is severely affected. The compressor has to work longer and, therefore, the system will use more power.
A rise in condensing temperature from 35 to 40°C as a result of dirty coils can cut cooling capacity by 7% and increase power CONSUMPTION BY 10%WITH A NET COMPRESSOR EFFICIENCY REDUCTION of 16%. Such performance degradation in a 35kW unit operating for 2,000 hours in a year can increase operating costs by $250 per year.
Poor heat exchange of coils reduces system performance meaning air conditioning is less able to cope with extreme ambient conditions. As an illustration of this a study, focusing on practical maintenance, shows that on a typical 10.5kW rooftop UNIT IF EVAPORATOR AIRFLOW IS RESTRICTED BY 36%, THE CAPACITY DROP is 19.4%. In effect this changes the 10.5kW unit to an 8.8kW unit 3.
Equipment Life Cycle
Poorly performing coils also mean that other parts of the air conditioning system have to work harder or for longer resulting in reduced life cycles. With refrigerated air conditioning systems, compressors have to work harder and longer to achieve the required system performance. Poor coil performance in these systems can also lead to other problems that either reduce compressor life or in some circumstances cause catastrophic compressor failure. Likewise with water based systems, with decreased coil performance chillers, boilers and pumps all have to work harder. In addition, biological growth on coils can lead TO FIN CORROSION THAT OVER TIMEWILL SIGNIFICANTLY REDUCE THE COILS' performance to a point where they will need to be replaced.
Indoor Air Quality
In cooling coils the conditions often exist for the growth of microbiological contaminants. Contaminants, such as bacteria, MOLD AND FUNGI CAN COLONISE ON THE COOLING FINS IN AN AIR CONDITIONING systems creating toxic allergenic organic fragments known collectively as Macromolecular Organic Dust. This has been linked with various health complaints in buildings. The buildup of contaminants also reduces heat transfer effectiveness and SYSTEM EFFICIENCY. REGULAR CLEANING REDUCES THIS BUILDUP.
When and How to Clean
The HVAC HESS report The Measures 5, which underpins the HVAC HIGH-EFFICIENT SYSTEM STRATEGY STATES THAT "systems whose heat transfer surfaces have not been cleaned in the last three years an immediate energy saving of at least 10% is expected to be achieved following cleaning. ”
A visual inspection offers a good general indication of when coil cleaning is needed.
A more technical approach requires the measurement of the temperature difference between the air entering and the air leaving the coil and comparing this to the temperature differential expected given the operational circumstance of the coil. The expected temperature change will vary dependent on a range of variables and care should be taken with where and how the readings are taken. As such, this testing should be carried out by an experienced service provider.
Your air conditioning maintenance provider should be able to advise on how regularly coils should be checked for cleaning and how cleaning should be carried out. AIRAH Application Manual DA19 HVAV&R Maintenance provides guidance on cleaning for the various types of coils found in air conditioning systems. Cleaning can involve the use of compressed air or water sprays and the removal of biological contaminants and involve the use of carefully selected chemicals. Cleaning should be carried out by experienced service providers to ensure equipment is not damaged and air handling systems are not contaminated by the cleaning process.
IN ADDITION WHILE CLEANING COILS IMPROVES ENERGY EFFICIENCY, THE GREATEST BENIFITS ARE REALISED WHEN THE COILS ARE CONSIDERED IN THE CONTEXT OF THE WHOLE SYSTEM INCLUDING FILTERS, DUCTWORK, AIR INTAKES etc. Typically when building staff or HVAC contractors service a unit several tasks are performed. It will include cleaning the dampers and both the condenser and evaporator coils, changing TE FILTERS, TIGHTENING BELTS, INSPECTING AND SERVICING the fans, and verifying refrigerant charge levels as well as damper and economiser functionality.
|Posted on November 4, 2015 at 5:40 PM||comments ()|
Psalms 95:2 (KJV)
Let us come before his presence with thanksgiving, and make a joyful noise unto him with psalms.
|Posted on September 10, 2015 at 3:30 PM||comments ()|
September 28, 1542 Spanish discovery of California by Cabrillo
September 6, 1620 The Mayflower ship departed from Plymouth, England, bound for America with 102 passengers and a small crew.
September 9, 1776 The U.S.A. came into existence as the Continental Congress changed the name of the new American nation from the United Colonies to the United States.
September 4, 1781 City of Los Angeles founded by Spanish Governor Felipe de Neve
September 3, 1783 Treaty of Paris signed that ended the American Revolutionary War
September 7, 1860 Birth of the great self-taught, late-life artist Anna Mary Robertson "Grandma Moses" 1860-1961
September 25, 1897 Birth of William Faulkner (1897-1962), considered by many the greatest U.S. author
September 8, 1900 The worst weather disaster in U.S. history: a hurricane with winds of 120 mph struck Galveston, Texas, killing over 8,000 persons.
September 14, 1901 Eight days after being shot, President William McKinley died from wounds suffered during an assassination attempt. Theodore Roosevelt then took over the presidency.
September 2, 1945 President Truman proclaims V-J Day upon the surrender of the Japanese
September 14, 1982 Former actress, American born Princess Grace of Monaco died following a car accident.
The Montreal Protocol on Substances that Deplete the Ozone Layer (a protocol to the Vienna Convention for the Protection of the Ozone Layer) is an international treaty designed to protect the ozone layer by phasing out the production of numerous substances that are responsible for ozone depletion. It was agreed on 16 September 1987, and entered into force on 1 January 1989
September 11, 2001 The worst terrorist attack in U.S. history.
September 23 Autumn begins in Northern Hemisphere (Spring in the Southern)
Labor Day: First Monday of September
|Posted on June 2, 2015 at 4:55 PM||comments ()|
It's June already! A year will have passed on June 9 since we started Freedom Air Conditioning and Heating Compant LLC, what an AMAZING year this has been and it is all due to GOD blessing us with work and YOU, our valued customers that have made ths dream a reality. Thank you isn't a strong enough word but it is all that I have, I am eternally grateful to each of you for allowing Freedom Air Conditioning and Heating Company LLC to EARN your business and your trust. I am thankful that my wife has been so supportive of this venture at this stage in our lives.
please remember to replace your filters when you get your electric bill, keep weeds and grass from around your outdoor unit, cleanliness is next to godliness so remember to have your air conditioning system cleaned as soon as possible to prevent unnecessary problems and to keep your utility bills as low as possible.
Thank you again for a GREAT YEAR, may GOD bless each of you, and may GOD BLESS AMERICA!
|Posted on February 12, 2015 at 5:15 PM||comments ()|
It's February, the month commonly associated with LOVE! We at Freedom Air Conditioning and Heating Company LLC. would like to celebrate our love for our customers by SAVING YOU MONEY, please visit our "Specials" page for more details.
We also want to share a little history with you regarding this holiday with an exert from Wikipedia:
Saint Valentine's Day, also known as Valentine's Day or the Feast of Saint Valentine, is a holiday observed on February 14 each year. It is celebrated in many countries around the world, although it is not a holiday in most of them.
St. Valentine's Day began as a liturgical celebration one or more early Christian saints named Valentinus. Several martyrdom stories were invented for the various Valentines that belonged to February 14, and added to later martyrologies. A popular hagiographical account of Saint Valentine of Rome states that he was imprisoned for performing weddings for soldiers who were forbidden to marry and for ministering to Christians, who were persecuted under the Roman Empire. According to legend, during his imprisonment, he healed the daughter of his jailer, Asterius. An embellishment to this story states that before his execution he wrote her a letter signed "Your Valentine" as a farewell. Today, Saint Valentine's Day is an official feast day in the Anglican Communion, as well as in the Lutheran Church. The Eastern Orthodox Church also celebrates Saint Valentine's Day, albeit on July 6 and July 30, the former date in honor of the Roman presbyter Saint Valentine, and the latter date in honor of Hieromartyr Valentine, the Bishop of Interamna (modern Terni). In Brazil, the Dia de São Valentim is recognized on June 12.
The day was first associated with romantic love in the circle of Geoffrey Chaucer in the High Middle Ages, when the tradition of courtly love flourished. In 18th-century England, it evolved into an occasion in which lovers expressed their love for each other by presenting flowers, offering confectionery, and sending greeting cards (known as "valentines"). In Europe, Saint Valentine's Keys are given to lovers "as a romantic symbol and an invitation to unlock the giver’s heart", as well as to children, in order to ward off Saint Valentine's Malady. Valentine's Day symbols that are used today include the heart-shaped outline, doves, and the figure of the winged Cupid. Since the 19th century, handwritten valentines have given way to mass-produced greeting cards.
Happy Valentine's Day to ALL of our friends, family, and customers, may you experience true love on this day and every day!
|Posted on January 8, 2015 at 1:45 PM||comments ()|
Babylonians made promises to their gods at the start of each year that they would return borrowed objects and pay their debts.
The Romans began each year by making promises to the god Janus, for whom the month of January is named.
In the Medieval era, the knights took the "peacock vow" at the end of the Christmas season each year to re-affirm their commitment to chivalry.
At watchnight services, many Christians prepare for the year ahead by praying and making these resolutions.
There are other religious parallels to this tradition. During Judaism's New Year, Rosh Hashanah, through the High Holidays and culminating in Yom Kippur (the Day of Atonement), one is to reflect upon one's wrongdoings over the year and both seek and offer forgiveness. People may act similarly during the Christian liturgical season of Lent, though the motive behind this holiday is more of sacrifice than of responsibility, in fact the practice of New Year's resolutions partially came from the Lenten sacrifices. The concept, regardless of creed, is to reflect upon self-improvement annually.
At the end of the Great Depression, about a quarter of American adults formed New Year's resolutions. At the start of the 21st century, about 40% did.
Some examples include resolutions to donate to the poor more often, to become more assertive, or to become more environmentally responsible.
Popular goals include resolutions to:
Improve physical well-being: eat healthy food, lose weight, exercise more, eat better, drink less alcohol, quit smoking, stop biting nails, get rid of old bad habits
Improve mental well-being: think positive, laugh more often, enjoy life
Improve finances: get out of debt, save money, make small investments
Improve career: perform better at current job, get a better job, establish own business
Improve education: improve grades, get a better education, learn something new (such as a foreign language or music), study often, read more books, improve talents
Improve self: become more organized, reduce stress, be less grumpy, manage time, be more independent, perhaps watch less television, play fewer sitting-down video games
Take a trip
Volunteer to help others, practice life skills, use civic virtue, give to charity, volunteer to work part-time in a charity organization (NGO)
Get along better with people, improve social skills, enhance social intelligence
Make new friends
Spend quality time with family members
Settle down, get engaged/get married, have kids
Try foreign foods, discovering new cultures
Pray more, be closer to God, be more spiritual
Be more involved in sports or different activities
A comprehensive study commissioned by Australian comparison website finder.com.au in 2014 of more than 2,000 people found that 42% of participants set themselves a New Years' Resolution however, most failed at their goals. In fact, the study showed that almost two in three people (62%) didn't succeed with their resolutions. Interestingly, out of those who did achieve their resolutions three in four participants (76%) believed that sharing their goals, for example on a social networking service, helped reach them.
The most common reason for participants failing their New Years' Resolutions was setting themselves unrealistic goals (35%), while 33% didn't keep track of their progress and a further 23% forgot about it. About one in 10 respondents claimed they made too many resolutions.
A 2007 study by Richard Wiseman from the University of Bristol involving 3,000 people showed that 88% of those who set New Year resolutions fail, despite the fact that 52% of the study's participants were confident of success at the beginning. Men achieved their goal 22% more often when they engaged in goal setting, (a system where small measurable goals are being set; such as, a pound a week, instead of saying "lose weight"), while women succeeded 10% more when they made their goals public and got support from their friends.
It is also noted that talking with a counselor about setting goals and new year resolutions can help people keep their resolutions.
At FREEDOM AIR CONDITIONING & HEATING CO. LLC we like to keep it simple, Our Resolution is to Save YOU Money on ALL of your air conditioning and Heating needs through out the year, this is a goal that we know we can achieve with YOUR help.
Happy New Year everyone, may GOD bless us all!
|Posted on December 5, 2014 at 8:55 AM||comments ()|
During this time of trying to find the perfect gift for the ones that you love, we need to remember that perfect gift that was given to us so long ago and keep the true meaning of Christmas in our hearts and minds. The following comes from Luke Chapter 2...Enjoy! And may GOD bless each of us with HIS spirit this year.
2:1 And it came to pass in those days,
that there went out a decree from Caesar Augustus that all the world should be taxed.
2:2 (And this taxing was first made when Cyrenius was governor of Syria.)
2:3 And all went to be taxed, every one into his own city.
2:4 And Joseph also went up from Galilee, out of the city of Nazareth,
into Judaea, unto the city of David, which is called Bethlehem;
(because he was of the house and lineage of David:)
2:5 To be taxed with Mary his espoused wife, being great with child.
2:6 And so it was, that, while they were there,
the days were accomplished that she should be delivered.
2:7 And she brought forth her firstborn son,
and wrapped him in swaddling clothes, and laid him in a manger;
because there was no room for them in the inn.
2:8 And there were in the same country shepherds abiding in the field,
keeping watch over their flock by night.
2:9 And, lo, the angel of the Lord came upon them,
and the glory of the Lord shone round about them: and they were sore afraid.
2:10 And the angel said unto them,
Fear not: for, behold, I bring you good tidings of great joy, which shall be to all people.
2:11 For unto you is born this day in the city of David a Saviour, which is Christ the Lord.
2:12 And this shall be a sign unto you;
Ye shall find the babe wrapped in swaddling clothes, lying in a manger.
2:13 And suddenly there was with the angel a multitude of the heavenly host praising God, and saying,
2:14 Glory to God in the highest, and on earth peace, good will toward men.
2:15 And it came to pass, as the angels were gone away from them into heaven,
the shepherds said one to another, Let us now go even unto Bethlehem,
and see this thing which is come to pass, which the Lord hath made known unto us.
2:16 And they came with haste, and found Mary, and Joseph, and the babe lying in a manger.
|Posted on November 17, 2014 at 4:10 PM||comments ()|
This is the time of year that we reflect back over the year and acknowledge what we are thankful for. We at Freedom Air Conditioning and Heating Company understand that the one true GOD comes first in all things, we have a love for GOD, our families, and our GREAT Nation. It is only appropriate that at this time we relay a book from the bible to you here:
Make a joyful noise unto the LORD, all ye lands.
Serve the LORD with gladness: come before HIS presence with singing.
Know ye that the LORD HE is GOD: it is HE that maketh us, and not we ourselves; we are HIS people, and the sheep of HIS pasture.
Enter into HIS gates with thanksgiving, and into HIS courts with praise: be thankful unto HIM, and bless HIS name.
For the LORD is good; HIS mercy is everlasting; and HIS truth endureth to all generations.
HAPPY THANKSGIVING from all of us to all of you and your families!
|Posted on July 4, 2014 at 4:30 PM||comments ()|
Freedom Air Conditioning and Heating Company LLC would like to take a moment to give some facts regarding our Independence Day Celebration or 4th of July Celebration as some call it.
We would also like to thank ALL of the military men and women who have served or are serving today, from the war for independence, to Iraq and Afghanistan today, those who are stationed at home and abroad that allow us to live in the GREATEST country on the planet of the earth, may GOD bless each and every one of you! Happy Birthday America!
The Declaration of Independence
We celebrate American Independence Day on the Fourth of July every year. We think of July 4, 1776, as a day that represents the Declaration of Independence and the birth of the United States of America as an independent nation.
But July 4, 1776 wasn't the day that the Continental Congress decided to declare independence (they did that on July 2, 1776).
It wasn’t the day we started the American Revolution either (that had happened back in April 1775).
And it wasn't the day Thomas Jefferson wrote the first draft of the Declaration of Independence (that was in June 1776). Or the date on which the Declaration was delivered to Great Britain (that didn't happen until November 1776). Or the date it was signed (that was August 2, 1776).
So what did happen on July 4, 1776?
The Continental Congress approved the final wording of the Declaration of Independence on July 4, 1776. They'd been working on it for a couple of days after the draft was submitted on July 2nd and finally agreed on all of the edits and changes.
July 4, 1776, became the date that was included on the Declaration of Independence, and the fancy handwritten copy that was signed in August (the copy now displayed at the National Archives in Washington, D.C.) It’s also the date that was printed on the Dunlap Broadsides, the original printed copies of the Declaration that were circulated throughout the new nation. So when people thought of the Declaration of Independence, July 4, 1776 was the date they remembered.
In contrast, we celebrate Constitution Day on September 17th of each year, the anniversary of the date the Constitution was signed, not the anniversary of the date it was approved. If we’d followed this same approach for the Declaration of Independence we’d being celebrating Independence Day on August 2nd of each year, the day the Declaration of Independence was signed!
How did the Fourth of July become a national holiday?
For the first 15 or 20 years after the Declaration was written, people didn’t celebrate it much on any date. It was too new and too much else was happening in the young nation. By the 1790s, a time of bitter partisan conflicts, the Declaration had become controversial. One party, the Democratic-Republicans, admired Jefferson and the Declaration. But the other party, the Federalists, thought the Declaration was too French and too anti-British, which went against their current policies.
By 1817, John Adams complained in a letter that America seemed uninterested in its past. But that would soon change.
After the War of 1812, the Federalist party began to come apart and the new parties of the 1820s and 1830s all considered themselves inheritors of Jefferson and the Democratic-Republicans. Printed copies of the Declaration began to circulate again, all with the date July 4, 1776, listed at the top. The deaths of Thomas Jefferson and John Adams on July 4, 1826, may even have helped to promote the idea of July 4 as an important date to be celebrated.
Celebrations of the Fourth of July became more common as the years went on and in 1870, almost a hundred years after the Declaration was written, Congress first declared July 4 to be a national holiday as part of a bill to officially recognize several holidays, including Christmas. Further legislation about national holidays, including July 4, was passed in 1939 and 1941.
|Posted on June 10, 2014 at 1:50 PM||comments ()|
The "FAN" setting is selected at the air conditioner thermostat..........Instead, it should always be set on "AUTO". Set to cool on FAN, the blower pushes air through the ductwork continuously while the compressor cycles on and off. Moisture removed from the air while the compressor runs is reintroduced to the house when the fan alone runs between compressor cycles. Don't let this happen! Don't set the system on "FAN"! Set to cool on AUTO, humidity is kept lower, costs are much lower and comfort is higher. If your ducts are leaky (and most are) the FAN setting is especially costly to you.
The air conditioner's air filter is clogged...........Air flow is restricted. When air flow is restricted your HVAC (Heating, Ventilating and Air Conditioning) system runs less efficiently. A clogged filter increases costs, reduces comfort and can lead to costly equipment failures. When air flow is severely restricted, ice grows on the air conditioner's evaporator coils, a condition that can precede "slugging" the compressor with liquid refrigerant. The resulting repair bill can exceed $1,000. Change the air filter religiously! It should be replaced monthly during summer and winter periods of heavy use.
The evaporator coils are clogged with accumulated dust.........Air flow is restricted. Problems that result are much like those described above for dirty filters. If you have central air conditioning, all the air in your house draws through the air conditioner's filter, then through the cooling (evaporator) coils. Generally the filter doesn't clean the air; its purpose is to protect the equipment, in particular the cooling coils. In spite of the filter the downstream coils gather dust and grime over time. Energy efficiency is degraded by about 5% each year as the coils get dirtier! Your costs go up while comfort goes down. Have a service technician check the evaporator coils yearly and clean them if necessary.
The air conditioner thermostat is set too low...........Often its operation is misunderstood. Your air conditioner runs no faster at a lower setting, it only runs longer. The recommended summer setting is 78 degrees. Set it 2 to 5 degrees higher when you're away in the day. Recent research in Florida reveals that home cooling costs increase 12% for each degree setting below 78 degrees. Your cooling costs can almost double if you set the thermostat at 70 instead of 78 degrees!
The central heat pump is simultaneously cooling and heating .............and the cooling cost triples! Overall this is a rare condition, but memorable to all involved because the summer bills get so stunningly high. A variety of thermostat and wiring problems can be the cause. For example, we've found situations where 5,000 watts of supplemental heating strips come on whenever the air distribution fan runs, winter or summer. The auditor detects the problem by running the cooling system alone (other appliances off at the breaker panel) and timing the meter spin to calculate power draw. A 5,000 watt overage is readily detected by this method.
Teenagers...........are full-sized human beings who deserve as much respect as people of other sizes and ages, even if they use a lot of energy per capita but don't yet pay the bills themselves. Small children, by contrast, are low to the floor and relatively comfortable at levels of summer heat that stress many adults.
Central heat strips turn on, off, on, off .......even when the hallway thermostat is set to OFF. With everything in the house off or unplugged and the water heater switched off at the breaker panel, the meter races, stops, races, stops. Because of a thermostat, control wiring or other wiring problem, the central electric heating strips (10,000 to 20,000 watts) are coming on even though the distribution fan is off and all is silent. Without the fan running, heat from the strips is not distributed. Heat builds up around the strips until a high-temperature safety switch is activated, turning them off. They cool. They come on again.........and so on. Another rare problem like #5 above, but costly when it happens.
The thermostat is out of calibration........and so is the thermometer on the thermostat faceplate. The system cools lower than the temperature selected by the resident. For example, the thermostat might be set on 78 degrees, but an accurate thermometer shows that it's actually cooling to 75 degrees. This is an extremely common situation – We've found thermostats as much as 10 degrees off. The simplest solution is to rest an accurate thermometer on top of the thermostat, find out how much it's off, and compensate accordingly when you select the desired indoor temperature.
The ceiling lacks adequate insulation..........Heat from the attic is conducting through to the house below. Improving ceiling insulation is one of the best investments you can make towards lowering your air conditioning costs in summer. If you're not sure what level of insulation you have in your attic, call your electricity provider and ask for an energy audit. The older your home, the more likely it is that its original level of insulation would now be considered inadequate. We still find some older homes with no insulation at all.
Humid outdoor air is leaking into the house........through cracks around doors and windows, electrical outlets, ducts, vents or fireplace dampers that don't seal tightly. In Florida homes about 38% of the air conditioner's work (and operating cost) goes to drying out this moist air leaking in from out of doors. Leaks in the ducts that supply cooled air to rooms will make this situation much worse, because the overall house air pressure becomes "negative' with respect to the out of doors whenever the air conditioner is running. In this condition the house sucks in warm, moist air whenever the air conditioning system runs. The system runs longer to compensate. Even more warm air is drawn in, which needs to be cooled......and so forth in a vicious cycle. Costs rise significantly.
Dogs have pulled air ducts apart beneath the house, cats have bedded for years in the ceiling insulation, possums have tugged open a crawl way where water pipes penetrate the floor and they're living in the hollow wall of the bath tub.........and so forth. Energy wise, the worst of these situations is where supply or return air ducts are disconnected in the crawl space beneath the house. Every summer at least one of our technicians reports finding the family dog comfortably housed in the return air plenum under a customer's house. It costs a lot to cool the outdoors!
The house is equipped with jalousie or awning windows designed for cross ventilation.........Instead the house is closed up for air conditioning. Or almost closed up: Unfortunately, these window types are notoriously leaky. In summer, the air conditioner must toil to dry as well as cool the air, and major air leaks cause major cost increases.
A rooftop power ventilating fan pulls hot air from the attic on summer days.......but a). The fan's thermostatic control is set too low (maybe 95 degrees instead of 115 degrees), so the fan runs more than it should; b). There's a lot of air leakage from the house across the ceiling to the attic, or bathroom and dryer vents open into the attic instead of passing through the roof, so that when the rooftop fan pulls air from the attic it also pulls air (expensively cooled air) from the house. An “Attic Tent” is an inexpensive item that can reduce the heat infiltration due to leaks around attic stairs.
The air conditioning system is not getting enough air returned from the house......for a variety of reasons. We've seen return air grills set in the floor that are partly or entirely covered by a rug, for example. In addition to increasing operating costs, inadequate volume of return air back to the indoor HVAC coil is a major factor in shortening the life of central air conditioners. Too little air across the indoor coil can potentially lower the coil temperature to the point of ice formation on the indoor coil. An air conditioner with its indoor coil covered with ice is in a "destruction mode"
The HVAC filter is located in a return duct plenum under the house.......and because it's so hard to get to, it's never changed. At some time in the past a plastic laundry bag was sucked into the return air system and is now plastered against the filter. Almost every energy auditor can tell of finding situations like this.
The HVAC air handler, located in a hallway closet, is pulling return air from the attic as well as the house........adding considerably to costs. Sometimes this situation is discovered where the resident previously had a gas or fuel oil furnace in a hallway closet. Originally, the furnace pulled its combustion air from the attic through an opening in the closet ceiling. When the resident later switched to a heat pump, the furnace was removed from the closet and replaced with the heat pump's indoor "blower-coil" unit. But the ceiling opening remained. The new closet unit was set up to pull return air through a grill in the closet wall into the closet space, then through a filter mounted in the blower coil unit. But it's pulling air from the attic as well as the house! Most auditors have a story of first finding this problem when, with the air conditioner running, they climbed a ladder, lifted the attic hatch and noticed house air rushing past them into the attic.
The air conditioning equipment is inefficient........for a variety of reasons. First, it may have been inefficient from the start. Equipment ten years old or older is likely to have an original efficiency rating of 7.5 SEER (Seasonal Energy Efficiency Ratio) or less. Today, Federal law requires manufacturers to achieve SEER 10.0 or higher for all split-system units, and SEER 9.7 for package units. What do these SEER ratings imply? You've probably already guessed: If your cooling cost is $600 a summer with a SEER 6.0 unit, your cost would be $300 a summer (for the same amount of cooling) with a SEER 12.0 unit. What other factors affect air conditioning efficiency? The big three are a). dirty coils, which at normal rates of dirt accumulation degrade efficiency by 5% each year; b). duct leaks, which in most Florida homes account for about 20% of air conditioning consumption; and c). improper charge of refrigerant. How common are these types of problems? In 1988 a widely cited Arizona study of residential air conditioners found the following:
75% of the condenser coils were dirty
70% of the units had improper refrigerant charge
55% of the evaporator coils were dirty
45% had dirty blower wheels
35% had significant duct leakage
10% had a wrong motor or fan installed
The HVAC refrigerant charge is low.........or it's high. Either way degrades efficiency. In 1990 a field study of residential central air conditioners found 27% undercharged and 27% overcharged. Overcharging is worse. The unit's cooling ability goes down while the power draw goes up: The unit runs longer to do the job, and costs more per minute to run. Overcharging also stresses the compressor, with serious consequences for its lifespan. The compressor is the most expensive system component to replace
The air conditioner's compressor runs all the time........whether the indoor distribution fan runs or not. Rare.
The outdoor condenser is located beneath a wooden deck........and air flow is restricted. In summer, whatever heat is removed from the house by the air conditioning system is released to the outdoors from the condenser unit--that big metal box in the back yard. Hold your hand in the hot breeze from the propeller fan--it usually blows upward--and you'll get the idea. To work well it needs plenty of clearance from decks, bushes and folded lawn chairs. By the way, that hot air blowing from the outdoor condenser is not hot air from the house. It's outdoor air heated by passage across the hot condenser coils. The cleaner those coils are, and the easier it is for the heated air to get away from that unit, the better it works. Air conditioners and heat pumps only work well if kept clean!
There's a whole lot of cooking going on..........Meanwhile the air conditioning runs nonstop to cool the kitchen. To avoid this, a lot of folks cook outside in the summer, eat more fruits and salads, eat later in the evening..........or use a microwave oven! For the same cooking job, a microwave costs far less than half as much to operate as a standard electric oven, and doesn't heat the kitchen. Here's a comparison of costs to cook a meatloaf, from a study by Northeast Utilities (adjusted to our utility rates):
Oven Type Cost
Electric oven 17 cents
Electric convection oven 12 cents
Gas oven 10 cents
Electric frying pan 7 cents
Electric toaster oven 8 cents
Electric crockpot 6 cents
Electric microwave oven 3 cents
Someone's doing a mighty lot of clothes drying every day..........during the heat of the day, with a dryer located in an air conditioned utility room, vented to the outdoors. A clothes dryer has a powerful fan that whips air (house air in the case above) past the damp clothes at the rate of 150 to 200 cubic feet per minute (cfm). In a 1,500 square foot house with eight foot ceilings, a 200 cfm dryer can empty one house load of air every 60 minutes of operation. In summer, that's a lot of expensively cooled house air being heated by the dryer and blown out. Just as bad, that's a lot of lost house air that must be replaced by hot, damp outside air leaking in fast wherever it can: Through kitchen and bathroom vents, fireplace vents and dampers, around windows and doors, through recessed ceiling light fixtures, through electric plug and light switch plates, etc. For all the above reasons, it's best to locate the dryer in an uncooled utility room or garage.
The resident is equipped with a so-called "combination appliance" that uses a gas water heater to heat the water as well as the house (or apartment).........and in summer it keeps on sending heat to the house! Rare, but it happens as a result of failed electronic controls or system valves. Electric and gas costs both increase. The electric cooling cost typically doubles. For the energy auditor, higher than expected summer gas cost is often the telling clue.
Leaky supply or return air plenums.......greatly increase the cost of air conditioning. Using blower door technology to test Florida homes for duct leakage, almost all systems are found to be significantly leaky. The most common sites of leakage are the supply air and return air plenums, which are the air collecting boxes on the upstream and downstream sides of the blower-coil unit that distributes air around the house. In the supply plenum, air pressure is greatest; in the return plenum, air suction is greatest. Any leakage from these boxes is exaggerated by the extremes of positive or negative air pressure close to the fan. In the distribution system as a whole, if supply air leakage predominates, the air pressure in the rooms of the house becomes negative with respect to the outdoors. If return air leakage predominates, the air pressure in the rooms of the house becomes positive with respect to the outdoors. A negatively pressured house sucks in warm, moist outdoor air, burdening the air conditioner; a positively pressured house pushes out expensively cooled indoor air, losing it to the outdoors. Usually mere duct tape is inadequate to repair these high pressure plenum leaks--it simply comes loose. Repairs that last use a gluey paste called mastic, typically having a high content of embedded fiberglass fabric and high tolerance for variations in temperature.
Doors need weather-stripping........to prevent significant air leakage. The crack around all four edges of a standard door is 20 feet long. If the crack is 1/12" wide, the total "hole" size is 20 square inches, roughly the equivalent of a softball sized hole in the door! If the house is negatively pressured whenever the air conditioner runs because of supply duct leakage, that size hole admits a lot of warm, moist air for the air conditioner to cool and dry. A wide variety of weather-stripping materials are available at local hardware stores and home supply centers. You'll often find good instructions there too, either from staff or from how-to booklets.
Windows and doors need caulking........to prevent air leakage, for the same reasons discussed above. This is do-it-yourself work. Caulk is cheap, applying it is easy, but it takes time. Caulk cracks around window and door frames; cracks where masonry walls meet wood siding or trim; wall penetrations by pipes, meter box, dryer vent or exhaust vents, etc. Some all-purpose caulks are silicon, silicon-acrylic and siliconized acrylic latex.
Windows on the southwest or west side are fully exposed to the setting sun.......... and they need external and internal shading. In newer Florida homes sun entering the windows accounts for about 20% of the air conditioning load. In older homes, it can be as much as 30%. Use of interior shades, drapes or blinds reduces heat gain across the windows by about 20%. External shade (trees, awnings, sun screens) works even better. Some newer, high tech windows have special tints or films that reduce the amount of heat transmitted across the window into the house. Most window manufacturers now offer high-tech windows with low-E coatings. A low-E coating is a microscopically thin, virtually invisible, metal or metallic oxide layer deposited on a window. In a double paned window the coated surface may be either the outer side of the inner glass or the inner side of the outer glass. In Florida the latter design works better. The coating acts to suppress radiative heat movement across the window by reflecting heat back into the home during cold weather and back to the outdoors during warm weather.
In some apartments and townhomes, the air conditioner's indoor component (the blower coil that distributes air to rooms) is located in a small closet, right over the electric water heater...............which in summer heats the passing air on its way to the a.c. cooling coils and fan. It helps to lower the water heater's thermostats to the lowest appropriate temperature (usually 115 degrees, or 125 degrees if the resident uses a dishwasher) and insulate the water heater.
The HVAC system has moisture in the refrigerant........and efficiency is reduced 5-15%.
The HVAC system draws warm, moist outdoor air through an unsealed PVC chase.......that routes refrigerant lines through the slab. Costs rise as the air conditioner works to cool and dry outdoor air admitted to the system by this and other routes.
Schoolchildren are home from school all summer.........and the bill goes up.
The clothes dryer vents lint onto the air conditioner's outdoor condenser coils........The system, hampered in its ability to release heat, runs longer and longer.
The dryer vent itself is clogged with lint..........and it takes longer and longer to dry a load of clothes. With the vent clogged, the clothes get a hot, damp tumbling, but little moisture is removed.
The small pump on a water heating waste heat recovery unit runs nonstop.........whether the air conditioner is running or not. This can get pretty costly, especially if the water heater is a long way from the air conditioner's outdoor condenser.
The air conditioner's outdoor condenser sits baking in the sun........increasing its operating cost. A north side location for this unit is recommended. It's possible to shade it with trees, but remember that the condenser needs plenty of "breathing room".
The pets have special requirements for cooling.............
Vines, bushes, tall grass, leaves, litter or lawn chairs cover the air conditioner's outdoor condenser unit.........so it can't release heat.
The house is very large.........and so is the cost to cool it. There's more volume to heat and cool. Larger homes generally have higher utility costs, all things considered.
The garage was converted to a family room.........without insulating the walls or ceiling. Now it's the hottest room in the house, and that's where the TV is located and the family spends the most time. To make it comfortable, the family turns down the thermostat setting for the whole house. Costs rise.
The air conditioner is oversized for the house..........so that it cools powerfully but doesn't run long enough to dry the air. The result is a cool, damp interior that doesn't feel right. To improve comfort, the resident lowers the thermostat setting a few degrees and the system runs longer. This dries the air but overcools it. Costs rise. Everyone should know this about air conditioning: Bigger isn't better. An oversized air conditioner cycles on-and-off frequently, removes less moisture and wastes energy. A system correctly sized for your house will run longer for less cost, dry the air better and give greater comfort than the next bigger size. Correct sizing is a particular concern in the low country and coastal Georgia, where we experience a very, very, very damp climate.
The fireplace damper is open, or there's no damper at all.........admitting outdoor air or losing indoor air. Costs rise in either case, especially if there are HVAC duct leaks, and there usually are. One of our energy auditors took an informal survey of his customers last spring, asking those with fireplaces whether their dampers are closed. Among those who thought it was closed, about 50% were wrong: It's open.
Air conditioning supply registers around the house are closed off...........and the house becomes negatively pressured with respect to the out of doors, so that warm, moist outdoor air is pulled in. Additionally, airflow across the HVAC evaporator coil is reduced. The system's energy efficiency and cooling capacity are reduced. That is, for a given amount of cooling work to be accomplished, the system's running cost per minute and the number of minutes required both increase. Don't close off vents. Repeat: If you have a central air conditioner or heat pump, don't close off vents. A lot of older federal and state energy brochures and booklets have advised closing off vents but now we know better. Leave ‘em all open.
Bedrooms or other rooms are closed off, with no way for air supplied to the rooms to return (as the air conditioner operates)........Each closed-off room becomes positively pressured while the remainder of the house becomes negatively pressured with respect to the outdoors. The result is exaggerated leakage to the outdoors from positively pressured closed rooms, and from the outdoors into the negatively pressured house areas. Leakage occurs through bathroom vents, fireplace vents and dampers, around windows and doors, through recessed ceiling light fixtures, through electric plug and light switch plates, etc.
An air conditioning supply duct leads to the garage..........where it simply wastes cool air to the "outdoors".
The air conditioning system's return air grill is set low on a wall and blocked by a chair, or its set in the floor where it's covered by a rug...........resulting in restricted return air flow and all the attendant problems.
A small pool or spa is situated literally inside the house........Rare, but unforgettable. Why not do this? Because of the phenomenal moisture problems that result, not to mention high air conditioning costs. Remember, the air conditioner works to remove moisture as well as remove heat. Even in normal circumstances about 38% of the air conditioner's work (and operating cost) is devoted to moisture removal.
The customer is attempting to cool the entire house with a variety of old, inefficient window air conditioners........Here's a topic that deserves a closer look. Our energy auditors have all observed that customers with window air conditioners usually have significantly lower bills than those with central cooling systems. Yes, lower. Why? Because only one or two rooms are being cooled, not the whole house. However, if four or five old window units are operating all summer to cool the whole house, then costs get high. Older window units often have energy efficiency ratings down around 5 EER; newer central systems are at least twice as energy efficient as that.
In the hallway ceiling there's a large whole-house fan with incompletely closed louvers.............It provides a major site of air leakage to or from the attic. If you have one of these fans and never use it, you'd do well to seal it from above and drape it with blankets of insulation.
The air conditioner's thermostat is near some source of heat........like a floor lamp. The thermostat gets fooled, it senses heat and calls for the air conditioner to run.....and run, and run.......Remember, small thermostat adjustments make a big difference to your cost. If your system cools to 73 degrees instead of 78, your cooling cost rises about 60%.
The hallway wall behind the thermostat is hot.......because hot air is being drawn down from the attic through that wall cavity whenever the air conditioner runs. This tricks the thermostat into calling for more and more cooling. Finding the pathway of air leakage and sealing it cures the problem.
The area where residents sit down to eat is heated by morning or afternoon sun streaming through a sliding glass door........and the whole house is cooled to a very low temperature in order to achieve acceptable comfort levels at that spot.
Old casement or awning style windows are deformed out of alignment and will not seal shut............allowing warm moist air to leak in, or expensively cooled air to leak out.
The house lacks shade on the east or west sides, or a mobile home sits fully exposed to the sun...........Shade trees can reduce air conditioning costs by up to 30%, and higher if it's a mobile home.
Summer maternity............usually brings with it a heightened concern for thermal comfort. Just ask any woman who's been pregnant through a summer. Somewhat lower than normal thermostat settings are usually desired.
A shade tree was removed........and air conditioning costs increased by up to 30% compared to last year. Shade is important!
Air conditioning ductwork in a hot attic is poorly insulated.......Attic heat conducts through to warm the cool stream of duct air.
The return air plenum box constructed of sheetrock is uninsulated and leaky and sits in a hot garage.........A fairly common finding.
All the components of the air conditioning distribution system, including the air handler, supply ducts and a long return duct, are located in a hot attic.........Lots of older homes have their air conditioning systems configured this way.
Windows lack inside shading devices (shades, drapes or blinds), or the devices are not consistently operated............These shading devices are tremendously important. Use them to block heat entry during summer days.
A room or wing or extension was added to the house, or a garage or porch was enclosed.........and the overall cooling costs go up.
The air conditioner's thermostat mounted on the hallway wall is not level.........Behind the thermostat's cover plate its operation usually involves one or two mercury-containing glass bulbs that tip left or right as the temperature adjustment lever is moved. When you adjust the lever "downward", calling for cooling, the bulb tilts and a small blob of mercury rolls over to make an electrical connection. If the thermostat is off-level the mercury roll-over is affected, and the thermostat's calibration can be thrown off. For example, maybe you've set the lever to 78 degrees, but because the thermostat isn't level the system cools to 75 degrees. Cooling costs rise by 15% to 24%. (Leveling the thermostat is fairly easy using adjustment screws behind the faceplate, but if you're at all uncertain about it, have it leveled when your unit is next serviced.)
Bathroom power vents are left running...........sending expensively cooled air to the out of doors. Run these vents only as long as needed to clear that one room of its moisture. If the bathroom is 10 feet by 12 feet with an 8 foot ceiling, it holds 960 cubic feet of air. Most bathroom fans remove about 50 cubic feet of air per minute. In the above example, nineteen minutes of fan operation sends out one roomful of air.
The residents left town for a summer vacation and were expecting the next utility bill to be low........but they left the air conditioner at its normal thermostat setting during their absence and the weather was hot. For many folks, the best practice is to set the air conditioner's thermostat up to 83 or 84 degrees when away. The system runs once in a while, preventing indoor humidity from getting too high.
Windows and doors are left open while the air conditioner runs........
While the family is away during weekdays, a laundry maid or housekeeper is at work around the house.........and she (or he) sets the thermostat below 75 degrees.
House has a package-unit central air conditioner at one end, supply and return ductwork beneath the house and a garage converted to an uninsulated TV/family room at the farthest distance from the air conditioner. A couple of ducts are added to the air distribution system to supply cool air to the family room.......This is a recipe for high bills in summer, but even higher in winter. The ductwork has the longest possible run--both ways--to cool the room that gets the most evening use. The walls and ceiling need insulation. The air conditioner's delivery fan is probably not powerful enough to handle the additional area, and the add-on ducts result in an imbalanced system that no longer delivers the requisite 400 cubic feet per minute of air (per ton of cooling capacity) across the air conditioner's evaporator coils. It all adds up to high cooling and even higher heating costs.
The air conditioning system is made up of mismatched components........ resulting in greatly lowered operating efficiency. The condenser section and evaporator section need to be properly matched, as specified by the manufacturer.
A newly added room is hot so the thermostat setting for the whole house is lowered........meanwhile, in the attic, the air supply duct to the new room is laid out and connected to the "boot" above the register, but was never connected into the main system. By an installation oversight, no air is delivered to the new room. Surprisingly, most of our energy auditors have found unconnected air ducts like this at one time or another.
The ductwork "boots" behind the registers are loose, or ducts have fallen away from the boots............and the system is cooling the crawlspace under the house.
Flex duct in the attic is kinked or flattened, diminishing air supply to particular rooms...........and the thermostat setting for the whole house is lowered to compensate. This kind of problem is especially significant if the rooms having insufficient air supply are the kitchen or family room. This is a common problem!
The air delivery system includes some length of panned floor joists which are leaky.......... The spaces between floor joists are sometimes modified for use as return ducts. This cavity is made into a duct by attaching sheet metal over the bottom of the joists and by capping the ends of the joist cavity. A leaky panned floor joist draws in air from the crawl space or basement. To remedy, seal using mastic. The ceiling fans run backwards, breezing upwards. They should breeze downward, so you feel the breeze.
Office in the home......This is becoming more common. Here's the power draw of some selected home office accessories, taken from a 1993 article in Home Energy:
Equipment Type Power Draw (Watts)
Copier 6 400
Personal computer 62 62
Video Monitor 62 62
Laser printer 80 200
Fax machine 14 30
Totals 222 752
How much this costs depends on activity levels. Suppose the copier, printer and fax machine are idle 23 hours and active 1 hour each day: Together with computer and monitor (let's say they are active 24 hours/day), monthly cost is about $15.